Welcome to our webstie
Main Information :
Series: JMM series
Product Name: MCB Circuit Breaker 2P 6A to 63A
Product or component type: Miniature circuit-breaker
Device application: Distribution – houses, offices, factories etc.
Poles description: 2 pole
Rated current: 40A
This MCB Circuit Breaker 2P 6A to 63A, we have poles 1 pole, 2 pole, 3 pole and 4 pole, the voltage is 230V/400V~ and current from 6A to 63A. It is with the widening of anti-skid handle, can fix with fork type busbar, the side with ventilation design.
Every breaker in a blister packing, then 5 pcs per color box, 60 pcs per carton.
30 to 45 days when we receive your 30% deposit.
Our MCB Circuit Breaker 2P 6A To 63A Operation
If the circuit is overloaded for a long time, the bi-metallic strip becomes overheated and deformed. This deformation of Bi-metallic strip causes, displacement of latch point. The moving contact of the MCB is arranged by means of spring pressure, with this latch point, that a little displacement of latch causes, release of spring and makes the moving contact to move for opening the MCB.
The current coil or trip coil is placed so that during short circuit fault the magneto-motive force (mmf) of the coil causes its plunger to hit the same latch point and make the latch to be displaced. Again, when operating lever of the miniature circuit breaker is operated by hand, that means when MCB goes off position manually, the same latch point is displaced as a result moving contact separated from fixed contact in the same manner.
It may be due to deformation of a bi-metallic strip, or increased mmf of a trip coil or maybe a manual operation, the same latch point is displaced and same deformed spring is released, which ultimately responsible for movement of the moving contact. When the moving contact separated from fixed contact, there may be a high chance of arc. This arc then goes up through the arc runner and enters arc splitters and is finally quenched. When we switch it on, we reset the displaced operating latch to its previous on position and the MCB is ready for another switch off or trip operation.
1.Q:Where is your company?
A: Our company is located in Foshan City, Guangdong. Address is : Longsheng south road, Leliu town, Shunde dist. Foshan city, Guangdong, China(528322)
2.Q: Which airport is the closest to you?
A: The closest airport to JUNON company is Guangzhou Baiyun Airport, it takes about one hour and 15 minutes. We can arrange car to pick up you from the airport or from the hotel you stay and send you back.
3.Q:Do you have OEM service?
A: Yes, we offer OEM service.
4.Q: How many employees do you have?
A: We have about 2000 employees
Buy high quality MCB Circuit Breaker 2P 6A to 63A at best price, come and enjoy our cheap price and quality service!
Hot Tags: MCB miniature circuit breaker 2p 6A to 63a, China, suppliers, manufacturers, factory, wholesale, for sale
Please make sure your contact information is correct. Your message will be sent directly to the recipient(s) and will not be publicly displayed. We will never distribute or sell your personal information to third parties without your express permission.